The Proper Use Of The Check Valve
In the hot water heating system in order to reduce accidents Water hammer can be set in the vicinity of the pressure relief valve bypass pipe between the water circulating pump pressure and suction pipe. In the circulating pump is running, because the outlet side of the pump suction pressure is higher than the pressure side of the valve was closed. The moment when the pump suddenly stopped, pump the water side pressure drastically reduced, while the suction side pressure is significantly increased, in this pressure difference, circulating pump suction side of the line of water that pushed the water side of the check valve to the pump pipeline system, thereby reducing the suction side of the pipe network pressure increased amplitude; to reduce and prevent water hammer damage. Means relief valve on the bypass pipe should be used with less resistance, open and flexible products. Relief larger diameter bypass pipe to reduce water hammer more powerful, can limit under pressure by transient calculations to determine the diameter of the economy.
Kaitai Valve Group is headquartered at Baoshan City Industrial Zone,Shanghai China, Also it is one of high-tech enterprises in Shanghai, a member of the Association of China General Machinery, and a regular supplier to some of the country’s major energy players such as China Petroleum & Natural Gas Corp, China Petrochemical, China Power and China Sea Oil etc.We mainly produce sales Ball Valve，Gate Valve，Globe Valve，Check Valve，Butterfly Valve，Plug Valve and Strainer.
We can supply the quotation and drawing of valves according to request of customers.
We can delivery valves in time as per our clients’ need.
We also provide the valves service of after-sales.
More valve product information：http://www.valveschina.net/